ePTFE gasket tapes for high chemical resistance—The connections to shell and tube heat exchangers pose immense challenges for the seals that are used because of both the chemically aggressive media and the frequent temperature load changes. Despite its excellent chemical resistance, polytetrafluoroethylene (PTFE) is not typically suitable as a sealing material in this case because the creep tendency of this material jeopardizes a reliable seal.
Shell and tube bundle heat exchangers generally include not only several connection pieces but also a shell cover flange with a significantly larger nominal diameter. The shell cover flange creates the seal to the tube bundle flange, which then seals the shell flange.
These connections are subjected to the full operating pressure and test pressure of dozens of bar and seal it from the environment. Oftentimes the tube bundles are arranged in several passes that are channeled by the use of partition plates. This requires a seal at the head of the heat exchanger and between the tube passes at the partition plates where the pressure difference is considerably lower. The numerous potential different arrangement of the passes requires specially adapted seal designs.
The sealing challenges that pertain to the shell cover flange position can be attributed to a combination of different conditions:
- High temperatures/pressures
- Temperature load changes caused by starting up and shutting down part of the process
- Complex sealing geometries including separators, often combined with large nominal diameters
- Chemically aggressive media
- Damaged sealing surfaces, due to corrosion or warping
- The economic necessity of minimizing downtime
- The requirement to document legal compliance
“Creeping“ Gasket Tapes Made of PTFE
Gasket tapes are occasionally used to seal the static connections to shell and tube heat exchangers – sealing materials with a defined width and thickness, but an undefined length. They offer a way of functionally connecting the junction points and can be shaped as desired at the point of installation.
Since the gasket circumference is completed at the time of installation, it is no longer necessary to completely dismantle the heat exchanger, removal of the tube bundle, for example. It is only important that the sealing surfaces be sufficiently accessible. Gasket tapes have been around in many different industrial fields for several decades.
This article is protected by copyright. You want to use it for your own purpose? Infos can be found under www.mycontentfactory.de (ID: 43333945 / Heat Transfer)